This tissue has following status: blue
Created: 13 Mar 2015
Links: #1319 AddCause for control value Out-of-range
Clause: 8 Data attribute semantic
Paragraph: Table 64
Category: Issue for edition 2 of this part
Issue: The range of configurable values are given by two attributes:
maxVal Defines together with minVal the setting range for ctlVal (CDC INC, BSC, ISC), setVal (CDC ING) or setMag (CDC APC, ASG).
minVal Defines together with maxVal the setting range for ctlVal (CDC INC, BSC, ISC), setVal (CDC ING) or setMag (CDC APC, ASG).
It is not defined what happens if the values ctlVal, setVal or setMag are outside of the setting range.
For measured values we have out-of-range quality information. For settings we should define, that a value of ctlVal, setVal or setMag SHALL be always within the setting range.
Proposal: @part 6:
During system engineering and IED configuration it is the responsibility of the tool (engineer) to prevent a value outside.
values for ctlVal, setVal or setMag SHALL be always within the setting range.
In case of online overwriting any of these values, the server shall reject any value outside the setting range.