368 Mapping of analog setpoints (SP)
Created: 24 Aug 2006
Status: In Force (green)
Part: Part 8-1 (2004)
Page: 84 and 86
Clause: 20.5 and 20.7 and 126.96.36.199
Category: Issue for edition 2 of this part
The tables show mapping of 7-2 "Value" into xxx$ctlVal. It does not allow the setMag structured attribute of setpoints to be used.
Indicate that 7-2 "Value" is mapped to the underlying CDC of the control object. For example, part of PDIS.PoRch setpoint data is mapped to PDIS.PoRch.Oper.setMag.f.
This also requires additional text (and another Table) in Annex E.4 near E.4.4 indicating values for setMag.
Note: To see attachments you have to log-in first.
||13 Oct 06
||In Force (green)
-Change 3 place 'Where <xxx> is the appropriate CDC (e.g. ctlVal or setMag)' to 'Where <xxx> is the appropriate CDC (e.g. ctlVal or setMag$f or setMag$i)'
-The suggestion for Table E.8 shows mxVal for CDC APC. This CDC has only setMag and not mxVal. The M/O/C entry for this line should be as 'M for APC and ASG'.
-Tables E.9 and E.10 should be modified like E.8 shown above
Replication of Bruce's comment.
|12 Oct 06
Agree with Bruce's second comment.
||12 Oct 06
||29 Sep 06
agreed...Proposed text changes are attached.
||07 Sep 06
Privacy | Contact | Disclaimer
Tissue DB v. 188.8.131.52