1858 Usage of Beh test/blocked when performing protection tests
Created: 06 Jan 2023
Part: Part 7-1 (2020; Edition 2.1)
Page: 62, 66
Clause: 7.7.3, 7.8.4
The paragraphs illustrate very basically the usage of Beh during test.
Consider updating 10-3 with regard to usage of Beh test/blocked, and consider updating the clause to indicate that in case of test, when the breaker is in test/blocked, the subscribers IEDs need most likely to be in simulation state and get a breaker position after a trip that match the scope of the test from the breaker simulator.
Privacy | Contact | Disclaimer
Tissue DB v. 18.104.22.168